NFPA 96 Standards
The National Fire Protection Association regulations are specifically designed to limit the life safety concerns and fire hazards associated with commercial cooking equipment and rooftop grease containment*. At Averus, we take all the necessary steps to comply with these codes on your behalf. Along the way, we act as your consultant to make the process as smooth as possible.4-8.2.1
Rooftop terminations shall be arranged with or provided with the following:
c.) The ability to drain grease out of any traps or low points formed in the fan or duct near the termination of the system into a collection container that is noncombustible, closed to the elements, rainproof, structurally sound for the service to which it is applied, and will not sustain combustion. A grease collection device that is applied to exhaust systems shall not inhibit the performance of any fan. Exception: Grease containers that are evaluated for equivalency with the preceding requirements and listed as such.
8-3.1 Hoods, grease removal devices, fans, ducts, and other appurtenances shall be cleaned to bare metal at frequent intervals prior to surfaces becoming heavily contaminated with grease or oily sludge. After the exhaust system is cleaned to bare metal, it shall not be coated with powder or other substance. The entire exhaust system shall be inspected by a properly trained, qualified, and certified company or person(s) acceptable to the authority having jurisdiction in accordance with Table 8-3.1.
Table 8-3.1. Exhaust Cleaning Inspection Schedule:
TYPE OR VOLUME OF COOKING
|Systems serving solid fuel cooking operations||Monthly|
|Systems serving high volume cooking operations such as:24 hour cooking, charbroiling, or wok cooking||Quarterly|
|Systems serving moderate-volume cooking operations||Semiannually|
|Systems serving low volume cooking operations such as:churches, day camps, seasonal businesses, or senior centers||Annually|
8-3.1.1 Upon inspection, if found to be contaminated with deposits from grease-laden vapors, the entire exhaust system shall be cleaned by a properly trained, qualified, and certified company or person(s) acceptable to the authority having jurisdiction in accordance with Section 8-3.
3-2.3 Grease filters shall be listed and constructed of steel or listed equivalent material and shall be of rigid construction that will not distort or crush under normal operation, handling, and cleaning conditions. Filters shall be tightfitting and firmly held in place.
4-3.1 Openings shall be provided at the sides or at the top of the duct, whichever is more accessible, and at changes of direction. Openings shall be protected by approved access panels that comply with 4-3.4.4. Exception: Openings shall not be required in portions of the duct that are accessible from the duct entry or discharge.
5-1.1 Approved upblast fans with motors surrounded by the airstream shall be hinged, supplied with flexible weatherproof electrical cable and service hold-open retainers, and listed for this use.